Ground Mount

The adder for a ground mount is 0.60 cents. Select ground mount under roof type in Frank

A ground mounted array must follow the listed specifications:


 * 7 Kilowatt (KW) minimum system size
 * No more than four rows (insert image)
 * 75 feet of trenching is included. If the MPU is more than 75 feet away, a trenching adder for the additional trenching required must be added in Frank.


 * Ground mounts cannot be installed on leach fields or on top of septic tanks.
 * Ground mounts must be 10 feet away from neighboring property lines and vegetation.
 * Tilt/pitch is 16-20 degrees unless on a hill
 * If a ground mount is on a hill it must follow the slope and contour of the hill